dixell. DEFAULT SETTING VALUES. تا تا تست ه تا تن تا نا م ع. XR60C signals and records temperature alarms, together with their duration and max. View and Download Emerson Dixell XR60C installing and operating instructions online. Digital controller with defrost and fans management. Dixell XR60C. Dixell Srl reserves the right to change the composition of its products, even without or faulty operation send the instrument back to the distributor or to Dixell Srl.
|Published (Last):||6 November 2018|
|PDF File Size:||5.50 Mb|
|ePub File Size:||5.76 Mb|
|Price:||Free* [*Free Regsitration Required]|
Ensure that the wires for probes, loads and the power supply are separated and far enough. Hold the SET key pressed for more than 3s, while the recorded alarm is displayed.
electronic controller DIXELL XR60C-0N1C0 mounting measurements 71x29mm 12V voltage AC/DC
Check the supply voltage is correct before connecting the instrument. The instrument is fully configurable. Don’t show me this message again. Add to my manuals Add. Push and immediately release the SET key or wait for 5 seconds to. At the end of defrost dripping time is started, its length is set in the FSt parameter. Comments to this Manuals Your Name. Don’t have an account?
electronic controller DIXELL XR60C | horecatiger
The instrument shall not be used diell purposes different from those described hereunder. Two defrost modes are available through the “tdF” parameter: Do not expose to water or moisture: Djxell case of failure or faulty operation send the instrument back to the distributor or to “Dixell.
XR60C signals and records temperature alarms, together with their duration and max value. To display target set point; in programming mode it selects a parameter or confirm an.
To see the kind of alarm, the max min. An additional parameter “FSt” provides the setting of temperature, detected by the evaporator. Then the instrument displays the temperature once again. In case of fault in the thermostat probe the start and stop of the compressor are timed through.
If the alarm LED is on, an alarm has taken place.
Unidrive hs series; unidrive m series. Push and immediately release the SET key: The instrument must not be opened.
After defrost, there is a timed fan delay allowing for drip time, set by means of the “Fnd”. Other parameters are used to control the.
EMERSON DIXELL XR60C INSTALLING AND OPERATING INSTRUCTIONS Pdf Download.
Consider the maximum current which can be applied to each relay see Technical Data. The fan control mode is selected by means of the “FnC” parameter:. To print the manual completely, please, download it. By pressing ‘print’ button you will print only current page. This function managed by dxiell Fct parameter is designed to avoid short cycles of fans, that.
This xr60v is part of the product and should be kept near the instrument for easy and quick. In case of applications in industrial environments, the use of mains filters our mod. This is used to make sure circulation of air only. Enter text from picture: Got it, continue to print.
On the display the following message is shown: